|Features & Benefits
- Economical 2 x 2 ft. locking ceiling tile enclosure secures smaller APs from most vendors
- Attractive, textured, powder-coat finish matches many ceilings
- Interchangeable doors permit simple migration to new APs and antennas
- Enclosure back-box is an effective dust barrier to simplify ICRA procedure compliance
- Design: Economical ceiling tile enclosure designed for smaller APs with integrated antennas. AP mounts in interchangeable door. Fits into standard 2 x 2 ft. (U.S.) ceiling grid. Doors available for all leading AP vendor’s models (see Oberon’s Model 1046 configuration guide)
- Performance: UL listed for low voltage applications, and designed to meet NEC300-22 and 300-23 for plenum installations. OSHPD approved, OPM-0110-13. De-rate AP operating temperature range by 10°C when mounted in enclosure
- Locking, quick release interchangeable door for migration to other APs
- Firestop grommet for insertion into back-box, large enough for 2 Cat6A cables
- 1 in. trade size knockouts in four walls
- Construction: 20 ga. galvanized steel back-box. 18 ga. white, powder-coated steel flange and door. Solid back-box fills opening behind AP, creating an effective fire, smoke and dust barrier to simplify ICRA compliance
- Constructed to be compliant with City of Chicago Environmental Air (CCEA) plenum requirements
- Enclosure must be supported by the building structure, independent of the suspended ceiling, per NEC paragraph 300.11. Includes hanger wire
- Maximum weight inside enclosure is 25 lbs.
- For recessed grid ceilings, specify "–T" for tegular flange
- Size: 23.75 x 23.75 x 3 in. (603 x 603 x 76 mm). Back-box is 12.5 x 12.5 x 3 in.
- Specify "-600MM" for European (metric) ceiling (594 x 594 mm tile flange. All other dimensions are the same)
Standards for Safety
- UL 2416, Audio/Video, Information and Communication Technology Equipment Cabinet, Enclosure & Rack Systems
- CSA C22.2 NO. 60950-1-07 + Amd. 1 Amd. 2 Information Technology Equipment -- Safety. Part 1, General Requirements
- OSHPD Approval OPM-0110-13
- Width: 23.75 in.
- Height: 23.75 in.
- Depth: 3 in.
- Item Weight: 13 lbs.
- Shipping Weight: 17 lbs.
- Enclosure and door
- (1) Dual Cable Egress Firestop Kit (1 in. trade size conduit connector and firestop grommet)
- (2) Keys for lock
- (4) Hanger wires
- Installation instructions
Spec Sheet - oberoninc.com/index.php?option=com_content&view=article&id=2997&Itemid=399
Installation Instructions - oberoninc.com/images/_Instructions/Oberon_Model_1046-EXT3935_Instructions.pdf
Customer Prints - oberoninc.com/images/_Customer_Prints/Oberon_Model_1046-EXT3935_Customer_Print.pdf
Ceiling Tile Ordering Form - oberoninc.com/images/WebDocs/Ceiling_Tile_Ordering_Form.pdf
OSHPD OPM Drawing - http://oberoninc.com/images/WebDocs/Oberon_OPM.pdf
SECTION 27_21_33 DATA COMMUNICATIONS WIRELESS ACCESS POINTS
For Oberon product CAD files, contact customer service